To control electronic ballasts DALI and receivers DMX
EMDC-64M allows you to control up to 64 independent electronic ballasts DALI (Digital Addressable Lighting Interface) for fluorescent, LED and other lamps.
EMDC-64M allows the connection of up to 32 receivers DMX (Digital Multiplex) in one segment. When using repeaters, it can control up to 64 devices.
Control is possible from the iNELS BUS System via the system bus EBM or from the RF Control wireless transmitters. Selection of control (RF/EBM ) and controlled (DALI/DMX) interface is done via DIP switches on the front panel of the unit.
When used in the context of bus wiring (interface EBM) it is set using the IDM software.
Unit EMDC - 64M is powered by 230 V AC.
DALI bus is powered directly through the unit EMDC - 64M.
In the event that this is the last unit on the system bus EBM, it is necessary to use a termination resistor having a nominal resistance value of 120Ω.
DMX bus must be terminated at its end resistor with a nominal resistance value of 120Ω. Bus termination DMX -side EMDC - 64M is already implemented inside the unit.
Two members of the nominal resistance value of 120Ω adapted for easy insertion to the terminals come with the package. To end the system bus EBM, a member is inserted between the terminals EBM+ and EBM- on last unit on the bus. To end DMX bus termination is performed on the terminals of the last receiver (slave unit) e.g. DCDA-33M/RGB.
PRG button and MINI USB connector on the front panel are used to set up communication with the transmitter RF Control.
EMDC-64M in 3 module is designed for panel mounting on DIN rail EN60715.